VDE 0815/VDE 0816
Conductor: soft annealed copper wire diameter of
0,6 mm, class 1 (EN 60228)
Insulation: solid PE (EN 50290-2-23)
Twisting elements: 4 cores stranded to star-quads;
5 quads stranded to group
Colour code: according to VDE 0815
(for group stranding)
Cable core: group stranded
Core wrapping: termoplastic tapes
Screen: one side laminated aluminium foil (Al polyester) with a copper drain wire longitudinally applied under it.
Outer sheath: PVC sheath type YM1, acc. to
VDE 0207/3 (EN 50290-2-22).
Sheath colour gray RAL 7032.
VDE 0482-332-1-2/IEC 60332-1
Connection cable for use in electronics and in measurement, control and signal applications.
Can be used in dry and wet interiors for fixed installation on and under plaster.
Suitable for data transmission rates of up to
Not approved for power and underground installation.
The permissible temperature range:
– during installation: from -5°C to +50°C
– during operation: from -30°C to +70°C
Min. permissible bending radius: according to DIN VDE 0891 part 5
– during operation max. 10D
(D – outer diameter of cable)