HD 359 S2; IEC 60227-6
Nominal voltage: 300/500 V
Test voltage: 2,0 kV
Conductor: flexible strand consists of annealed copper wires class 6, according to
SRPS N.C0.015, IEC 60228.
Insulation: PVC compound, TI2 according to
HD 21.1/DIN VDE 0281 part 1 (YI2 acc. to
VDE 0207 part 4).
Colour code: acc. to HD 308 S2/VDE 0293-308
Core formation: cores are arranged in
groups of 2, 3 or 4 cores laid side by side.
Sheath: PVC compound, TM2 according to
HD 21.1/DIN VDE 0281 part 1 (YM2 acc. to
VDE 0207 part 5).
Sheath colour, grey or black.
Behaviour in fire: IEC 60332-1
In dry and wet conditions as control cable in
lifts, cranes, transported lines, machine tools, at medium mechanical tensile strain, when the cable is exposed to severe bending in one plane.
Permissible conductor temperature:
– max operating temperature +70°C,
– in short circuit (max 5 s), max +160°C.
Permissible environment temperature:
at laying and handling, min +5°C.
BENDING RADIUS (min.):
Smallest bending radius for permanently laid cable: 4D
(D – diameter of cable)