Standard: SRPS N.C5.220
DIN VDE 0276-603; DIN VDE 0276-627
HD 603 S1; HD 627 S1; IEC 60502-1
Nominal voltage U0/U: 0,6/1 kV
Test voltage: 3,5 kV
Conductor: wire or rope, class 1 or 2, according to SRPS N.C0.015, IEC 60228,
copper: type PP 45, or aluminium: type PP 45-A.
Insulation: PVC compound
Colour code: according to HD 308 S2;
Core: two or multi cores are stranded together.
Filling: non hygroscopic, non vulcanized rubber compound layer or thermoplastic compound layer.
Armour: lapped zinc-plated flat steel wire with contra helical zinc-plated steel tape.
Sheath: PVC compound (IEC 60332-1).
Sheath colour black (UV protection).
For laying in earth, indoors, in ducts, in the open air, in the water, when additional mechanical protection is required when cable is exposed to mechanical tensile strain during laying and use. For use in mines according to Technical standards for electrical plants, equipments and installations in mines, as well as horizontal and vertical installation in places where there is a height difference in mines, including methane holes.
Permissible conductor temperature:
– max operating temperature +70 °C,
– in short circuit (max 5 s), max +160°C.
Permissible environment temperature:
at laying and handling, min +5°C.
BENDING RADIUS (min.):
– multi core cables 12D (D – cable diameter).